|Code||Description||.pdf File||CAD File|
|FBINT||Flush Box Intumescent Pad 70x45mm|
|Product||Description||Plasterboard||Integrity (mins)||Insulation (mins)||Install|
|FBINT||Flush Box Intumescent Pad 70x45mm||19mm||120||90||Detail 1|
|FBINT||Flush Box Intumescent Pad 70x45mm||13mm||60||45||Detail 2|
- Fix flush box to framing. The flush box should be fitted against the plasterboard.
- Firmly insert FBINT with adhesive against back of flush box.
- Finish installation of wiring and fix face plate.
Installation Detail 1
Detail 1 is a back to back installation on a hollow wall system comprised of a 92mm steel frame and 1 x layer of 19mm Fireline on each side of the frame (total wall thickness of 130mm). The FBINT 1 was installed into a standard flush mount galvanised steel box, measuring approximately 75mm high x 50mm wide x 52mm deep.
Installation Detail 2
Detail 2 is a one side test on a 13mm plasterboard, 64mm frame and 13mm plasterboard setup (total wall thickness of 90mm). The FBINT was installed into a universal galvanised steel flush box, measuring approximately 90mm high x 50mm wide x 52mm deep.