- As per NZS 5807:1980
- Within one meter of each valve
- Near junctions
- In positions where hidden pipes reappear
- Maximum intervals of 8 meters on exposed pipes
- Remove/trim arrows as required to identify flow direction
NZS 5807:1980, AS 1345:1995
Surfaces should be smooth, clean and dry before application.
Clean surfaces by removing any debris and oily residue with isopropyl alcohol if required.
Textured surfaces will reduce contact area for the label and may impact adhesive performance.
Once applied do not reposition.
If applied to pipe lagging test the surface prior to full project application and/or check with lagging supplier.
Adhesives will not adhere to PTFE / Teflon like surfaces.